Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Below are the facts about 230v relay ,From right here you will get the solution specifics for instance description,feature ,price and some other finest related solutions ,you can get the particulars that which is the appropriate to purchase and find the discount cost.
if you should understand additional evaluations about 230v relay or other related product , it is actually simple to click the image and get much more information concerning the products which you fascinating,if you are interested the product ,you will need to study extra critiques.
There was an error connecting to the Amazon web service, or no results were found for your query.
If you found the write-up beneficial, please pass on our details and details for your buddies. Numerous from the troubles discussed inside the short article are certainly not broadly identified.
When you’d like a great deal far more articles like this, please take some moments to provide us your feedback. Despite the fact that %keywords% is commonly discussed, access to information about it may be tough to find. Please come back and have a look at us as soon as once again, we will have more high quality articles for your reading pleasure.
cccdgr3tate asked Question about my heating and aor unit?
I have a rheem heating and air unit and it stopped working about a week ago. My dad has changed the relay switch and has tested voltage on almost everything else you can test and we still can not get the unit working. Does anyone have any suggestions on what could be wrong.
And got the following answer:
There are many possiblities. Do you have 24v to the contactor (relay) from the thermostat? If not check transformer in furnace. The furnace is operated via a 120v curcuit which is seperate from the AC's condencing unit (outdoor unit with compressor) which is 230v. Check for 230v at both ends of contactor. Also check service disconnect on outside of house near condencing unit. Some have fuses behind the front panel. Does the fan in the condensing unit run? Was the unit running prior to this breakdown or is this new installation? If voltage is as should be you have an open curcuit. The likelyness of neither the fan or compressor operating when voltage is present is low unless the fan went bad first causing the compressor to overheat, short out,and fail under this condition. If so then it's time for a new one! You can check the compressor windings for opens with an ohm meter or continuity tester but first you must disconnect from voltage! Remove the cap on the compressor terminals and disconnect the three wires (mark them so you can replace them to there proper terminals later) and check for continuity between each of the terminals one pair at a time. Then check between each terminal and the case of the compressor. You want to find continuity between each terminal and the other two but none of them to the case. If you find any point between two terminals which doesn't have continuity that's your open curcuit and your compressor is history. The fan can be check in a similar manor BUT, be sure to disconnect the leads from the capacitor and discharge it (short across the terminals with an insulated screwdriver) before testing. Capacitors pack quite a shock even though the electricity to the unit is shut down so be careful.