Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Here are facts about 24 volt ac relay ,From right here you will get the item facts which include description,feature ,value and a few other very best related goods ,you will get the facts that that is the proper to buy and uncover the discount price.
when you may need to discover more evaluations about 24 volt ac relay or other connected solution,you could click the image and get a lot more info about the things that you interesting,if you will interested the product,it is essential to study a lot more testimonials.
There was an error connecting to the Amazon web service, or no results were found for your query.
You can in no way have too much information regarding such an important difficulty. Do you agree, Are you currently presently feeling far much better informed concerning the alternatives you could have, When all around you come about to be scratching their heads, it is a terrific feeling to have clear vision and know which path you take place to be heading.
If the above write-up helped your understanding of %keywords% please pass around the word about our web site. We would prefer to assistance everybody get a higher understanding on the selections they’ve obtainable.
My blower motor works fine when the AC is off, but when I turn it to cool from off, the furnace stops blowing and starts clicking. I recently changed the capacitor and am wondering if that could be part of the problem. I also just put in a digital thermostate from the originial dial type thermostat Someone said that the time delay board was messing things up and I didnt need it, could it be something else? If not, how can I remove the time delay board.
And got the following answer:
well first off you did what i would of done which is to change the t stat. the t stat is what sends the electrical signals to contactors or relays which are electrical mechanical devices that close to pass electricity on to the blower when a signal is sent to them which comes from the t stat. i bet it is a contactor or relay this is what the clicking is coming from. first off a contactor is a bigger version of a relay they are the same thing. now how do they work. first off your t stat sends out a 24 or low voltage. your furnace is 120 volts. now a relay has a coil of wire. when 24 volts is sent to this coil it sends out a magnetic field. now with that magnetic field two metal pieces or contacts close passing the 120 volts through making the blower and other things come on. the contacts are metal and when they close they make a click sound. so you are hearing clicking so it is probaly the blower relay that has gone bad. listen for the clicking and track it down and replace it and this should fix the problem if it doesnt then the wiring is messed up from the t stat to the components