Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinemulti.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Hi! Now you might be check about abb relay item exactly where you are going to come across the critiques, videos, links and photographs which will surely spark your interest. This site present information and facts that you just will have to have. There’s a whole array of sources that are waiting to be discovered. Please carry on reading and search more reviews or merchandise as below. We’ve got thrilling sources that had been gathered by our specialists in abb relay .hope you can get the top reviews and obtain the ideal item about abb relay.
I hope this write-up has offered you new insight on the topic and given you some things to take into consideration. Though there is certainly absolutely practically nothing new under the sun, the details and facts which you may have just completed reading is presented inside a fresh and fascinating way.
One issue is for confident, information on this subject is offered all over the web and this write-up is 1 of many articles obtainable around the subject. We adore writing on this topic and have presented our point of view. Definitely feel no cost of charge to look about and discover our web-site for a lot additional %keywords% information.
I Know there are equations for each diff relay ! but i have a problem how can i test the diff characteristic depending on those equations ?
And got the following answer:
It's always great to see answers from people who have no idea about the art and science of protective relaying... While the specific equations of your current differential relay will be given in the manufacturer's manual, you can still determine its major characteristics without the manual. Current differential relays use the concept of measuring the current flowing into and out of a device, and determining how much of that current is 'lost'. If this difference in current is excessive, the relay trips the breaker to de-energize the circuit(s). Usually, the discrimination is a percentage of the current flowing into the protected equipment, e.g. a 15% setting would trip for a difference or current 'loss' above that level. Since there may be measurement uncertainty, especially at low current levels, it is common for the trip characteristic to require a definite non-zero amount of difference current before tripping. (You wouldn't want a transformer differential to trip on magnetizing branch current.) Likewise, for tremendous levels of difference current, the relay may use an altered characteristic to provide faster tripping, or more security, depending on the application. The manufacturers usually provide very detailed descriptions of their relays. Look for ABB, Siemens, Schweitzer Engineering Labs (selinc.com), GE-Multilin. I would start by hooking up two 3-phase sets of current sources (the test set) to the relay and shoot a little current in it. Gradually increase the differential current until it trips. Do the same for higher "through" currents, and on the other phases. With enough testing, you will determine the characteristic. The manual will help you get the testing set up correctly. If you don't have a dual 3-phase test set, it may be possible to test the relay with a single-phase set, but only for a small number of the possible current differential relay configurations. Voltage differential relays work on basically the same principle, but they are limited in application. High impedance bus differential relays are a very different form of current differential relay. They rely on the saturation characteristics of matched sets of CTs to detect if a fault is within the bus protected zone (trip) or outside the zone (no-trip). These Hi-Z bus diff relays are basically over-voltage relays with a few extra features. Check with the engineer before twiddling...