Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Are you searching for information about auto relay panel, study the item critiques, we will tackle the diverse aspects, fundamentals along with other points of interest about auto relay panel. Lots of readers discover that this web-site is a good place to start if you need to get the prodct about auto relay panel.
We will supply detailed resources like critiques, pictures, articles, videos and hyperlinks that may possibly be of superior use in case you would like to make a more detailed study about it.” in case you wish to obtain far more information regarding auto relay panel. just see clearly as beneath.
There was an error connecting to the Amazon web service, or no results were found for your query.
Obviously, there is undoubtedly a whole lot further to understand about %keywords%. This brief write-up is just a begin, plus the next step is generally to accomplish some further analysis. In any case, the ideas in the short article set the stage to get a substantially more detailed therapy from the subject.
Forgive me for my lack of technical jargon. My boyfriend and I live in a two story apartment with separate air intakes per floor, but only one thermostat located downstairs. It seems there is only outdoor unit to run both floors. Living in Texas, in the summer especially, it's important that our a/c works and hasn't let us down. In fact, while others complain about their upstairs being hotter than down, ours always seems to be cooler, presumably due to the upstairs having aprox. half the square footage as downstairs. Our only problem is that, even when the thermostat is switched to the off position, the upstairs air return and air vents are all blowing. It's only blowing room temp. air since the unit is switched off, but why won't it stop blowing? Obviously I could just call maintenance and let them deal with it, but they're extremely slow to deal with problems, and have trouble understanding English, so I'm trying this route first. I took off the thermostat panel and it looks like all the wires are hooked up except a blue wire which is wrapped around the bundle of cords and not attached to anything, though there are three spots open for another wire. My other concern is, shouldn't the upstairs need a temperature sensor or some kind to know when to kick it off? As far as I know, the upstairs blower has always stayed on. Which is irritating when it becomes far too cold upstairs while it's fairly warm downstairs. Thanks you for any help.
And got the following answer:
Check on your thermostat for the fan switch. This is seperate than the heat/cool switch. Turn it to AUTO, this will cause the blower to come on and go off when the heat or a/c go on and off. Having it in the ON position will cause it to run constant. If the switch is in AUTO and still running, you probably have a fried relay, as this will cause the blower to remain running as well.