Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Below are particulars about changeover relay ,From here you can get the item facts like description,function ,price and a few other greatest associated solutions ,you can get the information that which is the appropriate to buy and obtain the discount price.
if you would like to study a lot more critiques about changeover relay or relevant item , it can be simple to click around the image and get more info concerning the things which you exciting,if you want to purchase the item ,you need to read far more evaluations.”
There was an error connecting to the Amazon web service, or no results were found for your query.
If you’d like to suggest connected points about %keywords% that may very well be featured within this blog, you may get in touch with us and we will happily seem into it. Really feel no expense to let us know, as we would like to create our web-site the prime resource web-site for our readers that are keen on %keywords%. We would like to know your thoughts in addition to other feedback to produce our weblog improved. Please really feel absolutely free to leave a comment or maybe a message. We would love to hear from you.
classic_stump asked Honeywell Thermostat with a Goodman Air Conditioner / Heat Pump How Do I Hook it Up????
I have a Honeywell Pro 4000 (TH4210D) thermostat with terminals labeled... E (emergency heat relay), Aux (auxiliary heat relay), Y (compressor contactor), G (fan relay), O (cool changeover valve), L (relay)*, R (L1 hot), B (heat changeover valve) and C (L2 common). *The L (relay) terminal is powered continuously when thermostat is set to Em Heat. The Honeywell guide also states to use either O or B terminals for changeover valve and install field jumper between E and Aux if there is no emergency heat relay. The Goodman 3 ton package unit with heat pump and 15kw heat strip has wires colored... Red (24v), Green (fan), Orange (Rev. valve), White (Heat 2nd), Brown (Heat 3rd), Yellow (cool), Blue (common). So, the main question is how do I make these connections up and what is the difference between the Auxiliary Heat Relay and the Emergency Heat Relay? Any and everyones help is greatly appreciated.
And got the following answer:
brown from unit to e...white from unit to aux...red from unit to r....green to g....yellow to y...blue to c.....do not put anything on L terminal... orange to o but if unit heats instead of cools or vice versa put orange on b...aux heat comes on while heat pump is running if it cannot heat the house without help and emergency heat turns outside unit off and just runs your electric heat....you do not need to put the jumper between e and aux...