Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Here are information about contactor relay ac ,From right here you will get the solution information which incorporate description,function ,price and some other best connected merchandise ,you can get the facts that which can be the best to buy and locate the discount price.
when you will need to study more critiques about contactor relay ac or other related product,you are able to click the image and get far more information concerning the items which you intriguing,when you are interested the product,you must read additional reviews.
There was an error connecting to the Amazon web service, or no results were found for your query.
You can in no way have an excessive amount of information about such an significant difficulty. Do you agree, Are you currently feeling far better informed concerning the options you might have, When all around you occur to become scratching their heads, it really is a terrific feeling to have clear vision and know which path you happen to become heading.
If the above write-up helped your understanding of %keywords% please pass on the word about our internet site. We would like to aid everyone get a higher understanding on the selections they have obtainable.
My blower motor works fine when the AC is off, but when I turn it to cool from off, the furnace stops blowing and starts clicking. I recently changed the capacitor and am wondering if that could be part of the problem. I also just put in a digital thermostate from the originial dial type thermostat Someone said that the time delay board was messing things up and I didnt need it, could it be something else? If not, how can I remove the time delay board.
And got the following answer:
well first off you did what i would of done which is to change the t stat. the t stat is what sends the electrical signals to contactors or relays which are electrical mechanical devices that close to pass electricity on to the blower when a signal is sent to them which comes from the t stat. i bet it is a contactor or relay this is what the clicking is coming from. first off a contactor is a bigger version of a relay they are the same thing. now how do they work. first off your t stat sends out a 24 or low voltage. your furnace is 120 volts. now a relay has a coil of wire. when 24 volts is sent to this coil it sends out a magnetic field. now with that magnetic field two metal pieces or contacts close passing the 120 volts through making the blower and other things come on. the contacts are metal and when they close they make a click sound. so you are hearing clicking so it is probaly the blower relay that has gone bad. listen for the clicking and track it down and replace it and this should fix the problem if it doesnt then the wiring is messed up from the t stat to the components