Are you looking for critiques about digital timer relay, study the item critiques, we will tackle the diverse aspects, fundamentals as well as other points of interest about digital timer relay. Several readers discover that this blog is an excellent spot to begin if you’d like to get the prodct about digital timer relay.
We will supply detailed sources like critiques, pictures, articles, videos and hyperlinks that might be of excellent use for those who wish to make a more detailed study about it.” if you want to acquire extra information about digital timer relay. just see clearly as under.
[amzn_multi_product_inline keyword=’digital timer relay’ count=’1′ page=’1′ sort=” category=”]
If you would like to suggest related points about %keywords% that might be featured within this weblog, you may get in touch with us and we will happily appear into it. Feel no expense to let us know, as we would like to make our web page the top resource web-site for our readers that are serious about %keywords%. We would like to know your thoughts as well as other feedback to create our weblog improved. Please really feel free to leave a comment or perhaps a message. We would adore to hear from you.
Bethney asked How do use the timer on my boiler setback control?
The control is a Varistat R.D. 601 temperature proportional setback control, the clock is analog. I talked to the manufacturer; they said this model is too old for them to support. The clock controls are not simple like those on an electric lighting timer. Also I would like your opinion on changing the other settings(ratio, etc.) from the defaults. The manufacturer did explain this to me, but I forgot the math. If you need it, I can send a digital image of the device.
And got the following answer:
I'm a homeowner in central NY State who is considering having an outdoor temperature setback control installed to reduce boiler water temperature during warm weather in order to save fuel oil. I have a oil fired 105MBTU hot water boiler with three baseboard heat zones and one indirect hot water heater zone. Boiler water is set at 180 degrees and the indirect hot water heater is set at 130 degrees. The three heating zone thermostats and hot water control are connected to four relays that turn the four circulators on and off as needed. There is no circulator that runs all the time. The boiler turns on and off as needed to maintain 180 degree water. This is not a condensing type boiler. The system works very well, but I believe I could save some money, by maintaining a lower boiler water temperature in the summer. I believe the boiler water temperature would have to be maintained at 140 degrees or above in order to heat the domestic hot water and avoid condensation of flue gas in the boiler and masonary (clay liner) chimney. what do you think? Is this worth exploring? Thanks for your help.
[amzn_multi_product_inline keyword=’digital timer relay’ count=’4′ page=’1′ sort=” category=”]