I know you have to desire to find out how over voltage protection relay operates and that is finest to get, Does not it baffle your thoughts a bit, Does not it spark your curious mind, and make you feel incessantly about it, Are you currently enthusiastic about finding out details, trivia along with other exciting information about it, You’ve got come for the proper location mainly because each and every so frequently we update this site with numerous details about over voltage protection relay. you may study the solution information and evaluations as blelow,locate the very best to get having a discount value .
[amzn_multi_product_inline keyword=’over voltage protection relay’ count=’1′ page=’1′ sort=” category=”]
Bookmark our net web page and please come back and have a look at us quickly. We’ve other articles, just like the 1 above, which may be good to obtain your mind looking at %keywords% within a completely distinctive way.
Why not sign up for our e-mail notifications in order that you happen to be able to become informed ideal away we post by far the most recent info, Please share your feedback and add for the expanding debate on %keywords%: there are thousands of readers waiting to study your thoughts.
At work we have an exhaust extraction fan that has a 15 HP motor. It is showing a draw on two legs at start up of over 200 Amps leveling to 35 amps once at speed. The third leg has only a 150 Amp draw leveling to around 30 amps. Is this normal? It is causing the thermal protection device to trip off. Once it gets to speed it is fine, I think, but by then the thermal device is tripped off. Any suggestions as to the first check? This system has been in place for 10 years with no problems (or maintenance). The motor seems fine when it is running. The fan must be heavy because it takes a long time to stop once it has had power removed. It is up on a roof with limited access, I will be looking at it tomorrow. I didn't expect it here but only an hour old and already three fantastic answers! I'm going to leave it open and see how many more great answers there are out there! Thanks guys. I'm glad I took a breath and stepped back today and didn't start buying the wrong parts to throw at it. $$$$$$
And got the following answer:
USA NEMA standard motors have a code letter on the nameplate to indicate starting current, not a precise value. However 200 amps is in the range to be expected. The unbalance among the phases seems a little higher than expected. Check to see what the voltage is and how well balanced it is. Check the connections at the overload relay, starter, disconnect etc. Is this a new installation or an old installation that formerly worked properly? PS1 If the fan takes a long time to coast to a stop, it is probably a bit if a strenuous job for the motor to start it. It might not take a big change in the system to get to the point where the overload relay trips during starting. It could be bearings wearing out or dirt building up. It could be something like an increase in overall system load that reduced the supply voltage a little. It could be an increase in single phase loads that caused some unbalance in the three phase voltage. It could be a couple of shorted turns in one phase of the motor due to years of hard starting.
[amzn_multi_product_inline keyword=’over voltage protection relay’ count=’4′ page=’1′ sort=” category=”]