Warning: file_get_contents(/home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/templates/kefuang/inlinesingle.html) [function.file-get-contents]: failed to open stream: No such file or directory in /home/content/62/10983362/html/timer-relay/wp-content/plugins/amzn/amzntemplates.php on line 29
Here are the most important points about relay circuit breaker ,From right here you will get the product facts like description,function ,value and a few other greatest associated goods ,you will get the facts that which is the ideal to purchase and locate the discount price tag.
if you wish to find out a lot more testimonials about relay circuit breaker or relevant item , you could click the image and get additional info regarding the things that you interesting,when you are interested the product ,you have to study far more evaluations.
There was an error connecting to the Amazon web service, or no results were found for your query.
I hope this write-up has provided you new insight around the subject and offered you some things to take into consideration. Even though there is completely nothing at all new under the sun, the info and facts which you may have just completed reading is presented in a fresh and interesting way.
One point is for confident, information on this topic is offered all over the web and this write-up is 1 of plenty of articles accessible on the subject. We adore writing on this subject and have presented our point of view. Really really feel absolutely free of charge to look around and discover our web-site for any lot more %keywords% data.
Power asked On a gas furnace does the relay hot black wire go in the same terminal as the black hot wire transformer?
We are trying to get the furnace to turn off at the temp. the theromstat is set on. It has been running & not stopping on it's one We have had to use the circuit breaker to turn it off & on. My husband recently put a new transformer & relay in it & after doing that it won't stop running. So he is changing the wires in hope that this will fix it. Anyone have any knowledge about these wires? He has 2 black wires---one from the relay & one from the transform, tied into the hot. One wire at the relay comes out & goes into the furnace. There is a set of wires from the furnace that feed into something that is not related to the 120 coming in. When he rewired this he must have done something wrong that caused the furnace to not turn off anymore. Before he did any of this they furnance was going off & on every few minutes. It all started when he put a new thermostat & the thermostat is fine now except that we can't control the off & on button & the temperture. thank you very much! EDIT someone told my husband to take one wire at a time & disconnect it to see if it would keep running. Is this a safe way to find out which one is operating the thermostat?
And got the following answer:
Relays usually have both Normally Open and Normally Closed contacts (often marked NO and NC in that order). The coil wiring should not be critical, there's no polarity involved. If he removes either of the relay contact wires and the furnace stops running, then he may have connected them to the normally-closed contact, so leave the center (relay armature contact) alone and simply move the other wire from the NC to the NO terminal. As for safety, as long as he doesn't touch the bare wiring while the system is energized, and ensures that any disconnected wires don't touch anything else, it should be safe.