Below are particulars about relay switch pdf ,From right here you can get the item particulars including description,function ,cost and a few other most effective connected goods ,you can get the info that that is the right to get and uncover the discount price tag.
if you want to study additional critiques about relay switch pdf or relevant item , it is actually easy to click on the image and get a lot more information about the products that you intriguing,if you need to buy the item ,you will need to study additional testimonials.”
[amzn_multi_product_inline keyword=’relay switch pdf’ count=’1′ page=’1′ sort=” category=”]
What do you think about the %keywords% web web-site, Let us know your thoughts and comments by leaving a reply on our entries or by sending us an email. We would appreciate to hear from you.
In case you really feel we missed an important update, let us know and we will be pleased to produce a post!
jes asked how to wire an alternating relay?
Ive never wired one of these before. I wired it like I would a normal relay, switching the coil, but its not alternating. I found a schematic for it and I think I have it figured out but I wanted to get someone else's opinion. The schematic is at http://www.macromatic.com/literature/catalog/pdf/arp-1.pdf I think I need pin 4 always hot 3 is neutral pin 5 the float switch to turn it on (and alternate) jumper between 1 and 5 loads on 2 and 8 and just wondering are pins 6 and 7 a set of normally closed contacts?
And got the following answer:
You must be referring to ARP-SPDT relay Pin 4 is connect to the live line and pin 3 is connected to the common line (neutral is used when you have a 3 or more wire system with at least 2 live lines and one neutral). It is necessary to have pin 3 and 4 connect properly for this relay to operate properly. the power MUST ALWAYS be supplied to pins 3 and 4. If your float switch is a single pole single throw switch or a single pole double throw switch; then you MUST have the jumper from 1 to 5. You 2 loads are conected to pins 2 and 8 M1 and M2 are NOT necessarily motors but likely motor starter relays. The contacts in these alternating relays are NOT designed to control motor loads with high inrush currents like you get with sump pumps. they are rated at 10 amps Contact rating: 10A @ 240V AC/30V DC, 1/2HP @ 120/240V AC (N.O.), 1/3HP @ 120/240VAC (N.C.) Contact 1 to 2 is a normally closed contact and therefore should not exceed a load greater than 1/3 HP at 120/240 volts Even though contact 1 to 8 is a normally open contact, you still should not exceed 1/3 HP at 120/240 volts
[amzn_multi_product_inline keyword=’relay switch pdf’ count=’4′ page=’1′ sort=” category=”]